MicroLERT™ Ultra-Compact Hazardous Location LED Beacon- AC/DC
TOMAR’s MicroLERT™ Hazardous Location is a compact LED warning light engineered to per- form in the harshest environments. Providing bright visual warning where the potential for gases or dust to explode exist in abnormal conditions, the MicroLERT™ Hazardous Location is UL listed for Class I, Division 2, Groups A, B, C, and D. The AC models are also UL listed for Class II, Division 2, Group F and G, and Class III. Totally non-metallic, these warning lights are fully sealed for NEMA 4 capability in any mounting configuration—base up, down, or side positions. Their compact design makes them ideally suited where space consideration may be an issue. Key Features for the MicroLERT™ 5-year warranty Class I, Division 2 Groups A, B, C, & D Sealed construction UL Listed Wide AC and DC input voltage Lexan lens Steady-on or Flashing Surface, Pipe, or Thread mounts 5 LED colors – Amber, Blue, Red, Green, and White Potential Locations and Applications for the MicroLERT™ The MicroLERT™ is UL listed for Class I, Division 2, Groups A, B, C, and D. The AC models are also UL listed for Class II, Division 2, Groups F and G, and Class III. Typical applications include manufacturing plants, chemical and petrochemical processing facilities, sewage treatment plants, offshore and dockside installations, agricultural, commercial, industrial, mining, and marine facilities. MicroLERT™ Specifications Lamp Type: LED Flash Rate: 75 NEOBE® flashes per minute – each flash containing 7 rapid bursts of light (approximately 560 ms "on-time" and 240 ms "off-time") Voltage and Amperage: 200 mA @ 24 VDC Flashing; 420 mA Steady-burn 40 mA @ 120 VAC Flashing; 85 mA Steady-burn 20 mA @ 240 VAC Flashing; 45 mA Steady-burn Operating Temperature: -20°C to 45°C MicroLERT™ Product Options Available in either Flashing or Steady-burn mode, this model operates over a wide AC and DC input voltage range. The DC version operates from 10-100 VDC, and the AC version from 85-265 VAC. Model Description Voltage 270XF-12-80 Flashing Flange Mount 12-80 VDC 270XF-120-240 Flashing Flange Mount 120-240 VAC 270XS-12-80 Steady-On Flange Mount 12-80 VDC 270XS-120-240 Steady-On Flange Mount 120-240 VAC 290XF-12-80 Flashing ½” Pipe Mount 12-80 VDC 290XF-120-240 Flashing ½” Pipe Mount 120-240 VAC 290XS-12-80 Steady-On ½” Pipe Mount 12-80 VDC 290XS-120-240 Steady-On ½” Pipe Mount 120-240 VAC 295XF-12-80 Flashing ½” Thread Mount 12-80 VDC 295XF-120-240 Flashing ½” Thread Mount 120-240 VAC 295XS-12-80 Steady-On ½” Thread Mount 12-80 VDC 295XS-120-240 Steady-On ½” Thread Mount 120-240 VAC Helpful Links MicroLERT™ Hazardous Location Compact LED Warning Light - Product Brochure IS1172 - AC Models Installation & Maintenance Guide IS1173 - DC Models Installation & Maintenance Guide
LED Configuration: Steady-On or Flashing and Color
Steady-On-Amber, Flashing-Amber, Steady-On-Blue, Flashing-Blue, Steady-On-Green, Flashing-Green, Steady-On-Red, Flashing-Red, Steady-On-White, Flashing-White
Surface/Flange Mount, 1/2" Threaded Mount (Male), 1/2" Pipe Mount (Female), Surface/Flange Mount with Blackout Cap, 1/2" Threaded Mount (Male) with Blackout Cap, 1/2" Pipe Mount (Female) with Blackout Cap