Long Barrel Compression Lug 6 AWG 3/8" Stud | 90°C Tin-Plated Copper
Crimp It Right 6 AWG → Die Index 24 Blue This lug crimps with any 12-ton U-groove tool using the index-24 die — ours, or your matching die: Burndy® U5CRT — Milwaukee® 49-12-U006 — ILSCO® ILD-24, or T&B® Color-Keyed® index 24. The die embosses “24” into the finished crimp for inspection. Get the Matching DieShop 12-Ton CrimpersFull Die & Tool Chart The Conversions Tech long barrel one-hole compression lug terminates 6 AWG copper conductors to 3/8-inch studs. The seamless electro-tin plated copper construction provides corrosion resistance and stable contact resistance over service life. Long barrel geometry increases pull-out strength and supports full compression crimping for medium-duty power distribution, panelboard terminations, and industrial control applications. Blue color coding enables quick field identification without sight window requirements.Specifications Material: Seamless Electro-Tin Plated Copper Conductor Size: 6 AWG Stud Size: 3/8 Inch Barrel Type: Long Barrel Barrel Length: 1.125 Inch Overall Length: 2.195 Inch Pad Size: 0.875 Inch L x 0.532 Inch W x 0.087 Inch Thk Pad Holes: 1 Barrel Entry: Chamfered Voltage Rating: 600 V Temperature Rating: 90 Deg C Die Index: I-24 Color Code: Blue Cross-ReferenceEquivalent to long barrel one-hole compression lugs from major manufacturers including Burndy (YA6CL4), Panduit (LCA6-38-X), and Ilsco. Conversions Tech lugs are engineered to US specifications and produced under certified partner factory agreements to deliver equivalent electrical performance at reduced procurement cost.FAQWhat crimping tool and die are required for this lug?Use a compression tool with die index I-24. The chamfered barrel entry facilitates wire insertion; ensure the conductor is fully inserted to the barrel stop before crimping.Is this lug rated for 90°C conductor ampacity?Yes. The 90°C temperature rating matches standard THHN/THWN-2 and XHHW-2 conductor insulations, allowing full use of 6 AWG copper ampacity tables per NEC.