Honeywell #V110E1028, 1-1/4" Angle Valve for High Capacity Radiator
High Capacity Thermostatic Radiator Valves provide precise and automatic control of room temperature in two-pipe systems by modulating the flow of hot water or steam through free-standing radiators, convectors and other heating units with high capacity requirements Product Features Continually monitors and adjusts room temperature for consistent comfort and relief from under-heating and overheating. Designed with the higher capacity normally required by U.S.A. heating systems Valve seat discm which is made of resilient material (EPDM), ensures tight shutoff on steam or hot water systems. Nickel-plated bronze casted body with working parts in cartridge insert for ease of service Controls include sensor, setpoint dial and valve actuator; components may be integral or connected by capillary tubes. Require no electrical connections. All working parts are replaceable using service tool (MT100C1011) while valve remains in service, in-line, under pressure. Valves normally open without control mounted. Valves may also be used with MV110 Electric Zone Valve Actuator. Meet ASHRAE Standard 102-1989. Product Specifications Application Type : Precise and automatic control of room temperature in two-pipe systems by modulating the flow of hot water or steam through high capacity heating units when used with T104 Thermostatic Actuators Pipe Size (inch): 1 1/4 in. Pipe Size (DN): DN32 Body Pattern: Angle Capacity: high Capacity (Cv): 8 Cv Capacity (Btu/hr-steam): 193,000 Btu/hr Connection Type: Threaded Pressure Ratings (Hot Water (psi): 150 psi maximum Pressure Ratings (Hot Water (kPa): 1034 kPa maximum Pressure Ratings (Steam (psi): 15 psi maximum Pressure Ratings (Steam (kPa): 103 kPa Differential Pressure Ratings (psi): 17 psi maximum Temperature Ratings (F): 248 F Maximum Temperature Ratings (C): 120 C Maximum Materials (Body): Bronze Used With: T104 BTU Calculator