S&P Silent 100 CDZ Wall Fan - PIR / Timer / Indicator / Shutte - Rated 26l/s
Product Part Number SILENT-100-CDZ Product Overview The S&P SILENT-100 CDZ is a quiet-running 100mm axial extract fan designed to remove stale air, moisture and odours from bathrooms, toilets, en-suites and other small domestic spaces. It is suitable for wall or ceiling mounting and connects to standard 100mm circular ducting. An integrated passive infrared movement sensor automatically switches the fan on when movement is detected within approximately four metres. This provides demand-controlled extraction without requiring the user to operate a separate switch. The adjustable run-on timer allows the fan to continue operating for between 1 and 30 minutes after movement was last detected, helping remove residual moisture and odours once the room is no longer occupied. The fan motor is mounted on vibration-absorbing silent elastic blocks to reduce noise transmission into the surrounding wall or ceiling. It also includes an operation indicator and an automatic back-draught shutter, helping prevent outside air from entering when the fan is switched off. Technical Specification Manufacturer: Soler & Palau Product Range: SILENT Fan Type: Low-noise axial extract fan Application: Bathrooms, toilets, en-suites and other small domestic spaces Installation: Suitable for wall or ceiling mounting Window Installation: Possible with the appropriate optional window kit Duct Connection: 100mm diameter Maximum Airflow: 95m³/h Maximum Airflow: Approximately 26.4l/s Listed Rated Airflow: 26l/s Fan Speed: 2,400rpm Maximum Power Consumption: 8W Supply Voltage: 230V Frequency: 50Hz Sound Pressure Level: 26.5dB(A) at 3 metres under free-air conditions Movement Sensor: Passive infrared PIR sensor Maximum Detection Distance: Approximately 4 metres Run-On Timer: Yes Timer Adjustment Range: 1–30 minutes Operation Indicator: Pilot light Back-Draught Shutter: Automatic back-draught shutter Humidity Sensor: No Motor Bearings: Long-life ball bearings Motor Mounting: Vibration-absorbing silent elastic blocks Motor Protection: Integrated thermal overload protection Electrical Insulation: Class II IP Rating: IP45 Maximum Air Temperature: 40°C Housing Material: Injection-moulded plastic Colour: White Front Dimensions: 158mm × 158mm Overall Depth: 109.3mm Rear Casing Depth: Approximately 84.6mm Installation Depth: 79mm Spigot Diameter: 98.9mm Weight: Approximately 0.57kg