Elta Revolution SLCX ATEX Long Cased Axial Flow Fan The Elta Revolution SLCX is an ATEX rated long cased axial fan for duct mounted extract or supply where hazardous area compliance is required. It is built in heavy gauge steel with an anti static impeller design plus a protection rating of Ex h IIB+H2 T4 Gb for specified hazardous area duties. What makes the SLCX the right fit for hazardous area ventilation ATEX rated construction: designed to meet the requirements of the 2014/34/EU directive with classification to Ex h IIB+H2 T4 Gb Anti static impeller blades: carbon filled anti static blade material for hazardous area duties Robust long cased build: heavy gauge mild steel casing roll formed plus welded then dip galvanised after fabrication Adjustable pitch impeller: aerofoil impeller design with factory set blade angle to deliver maximum performance for the selected model Installer practical wiring access: external terminal box with IP55 protection for straightforward connection access Performance and range overview Standard sizes: 7 sizes from 355mm to 710mm Air volume flow rate: up to 6.8 m³/s depending on model Static pressure: up to 872 Pa depending on model Operating temperature: suitable for operation up to +40°C Availability: AC models Typical applications Chemical process ventilation Water and sewage treatment Material and gas waste duties Dust and paint extraction systems Battery room ventilation plus refrigeration related duties Important installation notes Zone suitability: the unit is not suitable for Zone 0 use Ambient conditions: designed for ambient temperature from -20°C to +40°C Mounting: can be mounted at any angle provided it is adequately supported plus accessible for future maintenance Start up checks: confirm impeller rotation plus airflow direction at initial start up Duct sealing: seal flanges properly to minimise leakage and maintain system performance Accessories and specification add ons Common accessories include AV mounts, bell mouth inlet, flanged silencers, flexible connections, impeller side guard, matching flanges plus mounting feet. Any controller used must be selected and installed in line with hazardous area requirements. Selection tip Confirm the hazardous area classification on site then match it to the ATEX code shown on the fan label plus the Certificate of Conformity. Once compliance is confirmed, select the correct size using airflow plus static pressure at your duty point from the performance data. Warranty: 12 months. Product Data, Performance & Dimension Sheet See the full SLCX performance range curves plus SFP, electrical data, sound data, dimensions plus accessories to help you specify the correct hazardous area model. Click here to download the full data, performance and dimension sheet. Click here to download the full data, performance and dimension sheet. Installation, Maintenance & User Guide Use this guide for safe installation, correct start up checks, sealing guidance plus the routine inspection schedule needed to maintain ATEX integrity over time. Click here to download the full installation, maintenance and user guide. Click here to download the full installation, maintenance and user guide. Looking to specify or purchase? Explore our full range of heat recovery ventilation units or contact Buy Ventilation for expert guidance on selecting the right system for your project.
AC 4 Pole Three Phase, AC 2 Pole Three Phase, AC 4 Pole Three Phase High Performance (4-3B), AC 4 Pole Three Phase High Performance (2-3B)