TC-PBFO01 Honeywell ControlNet Repeater Adapter Hazardous
type: Product
description: Honeywell TC-PBFO01 ControlNet Repeater Adapter for Hazardous Locations Fiber Module Capacity & Power Specifications Fiber Module Capacity: 2 fiber modules. Intrinsically Safe Power Channel (Ui): 9.5 Vdc, 1 A, Ci = 120 nF, Li negligible. Power Consumption: One power supply unit load. Power Dissipation: 8 W maximum. Internal & External Bus Interfaces Internal Bus (TTL): Uo = 5.4 Vdc, Io = 201 mA, Po = 1.09 W, Lo ≤ 0.45 mH, Co = 71 μF. External Bus (ControlNet): Uo = 5.4 Vdc, Io = 201 mA, AC coupled with high-pass filter (f ≥ 900 kHz). Communication Rate: 5 Mbit/s. Galvanic Isolation (per DIN EN 50020): TTL Bus / Power Supply, TTL Bus / ControlNet, ControlNet / Power Supply. Environmental & Operating Conditions Ambient Temperature: -20°C to 70°C (-4°F to 158°F). Storage Temperature: -20°C to 100°C (-4°F to 212°F). Maximum Relative Humidity: 95% non-condensing. Pollution Gas Test: Test Level G3 per ISA-S71.04-1985. Shock Test: 15g peak, 11ms duration. Vibration Test: 2g @ 10 Hz to 500 Hz per IEC 68-2-6. Protection Class: IP20 (requires IP54 or better housing for field installation). Physical Dimensions & Wiring Dimensions (H x W x D): 92 mm x 94 mm x 87 mm (3.6 in x 3.7 in x 3.4 in). Weight: 0.319 kg (0.70 lb). Wire Size (Power Terminals): 12 AWG (4 mm²) stranded max, 1.2 mm insulation max. ControlNet Cable: Belden 3092A (see Honeywell specifications for details). Standards & Certifications Conformity: DIN EN 50014:1992, DIN EN 50020:1994, DIN EN 50284:1997, DIN IEC 721, DIN EN 50081-2, DIN EN 50082-2, NAMUR NE 21. CE Conformity (Europe): TBD. CENELEC Classification: II (1) 2G EEx ia/ib IIB/IIC T4. ATEX Certification: DMT 99 ATEX E 036 X. Marked for all applicable directives. Installation Guidance Mount the Honeywell TC-PBFO01 on a DIN rail inside a suitable enclosure. Use an IP54 or higher rated housing when installing in hazardous field locations. Connect the ControlNet cables using Belden 3092A coax per Honeywell specifications. Install fiber optic modules into the …
brand: Honeywell
sku: TC-PBFO01
additional property: Title
  type: PropertyValue
  value: Default Title
offers: AggregateOffer
  low price: 218.00
  high price: 218.00
  price currency: USD
  offer count: 1
  offers: Offer
    price: 218.00
    price currency: USD
    availability: https://schema.org/InStock
    item condition: https://schema.org/NewCondition
    shipping details: OfferShippingDetails
    sku: TC-PBFO01

BreadcrumbList
item list element: Home
  type: ListItem
  position: 1
  item: /
item list element: www.nex-auto.com
  type: ListItem
  position: 2
  item: https://productregistry.org/merchant/www.nex-auto.com
item list element: TC-PBFO01 Honeywell ControlNet Repeater Adapter Hazardous
  type: ListItem
  position: 3
  item: https://productregistry.org/product/qQM6badq