TC-PBFO01 Honeywell ControlNet Repeater Adapter Hazardous
Honeywell TC-PBFO01 ControlNet Repeater Adapter for Hazardous Locations Fiber Module Capacity & Power Specifications Fiber Module Capacity: 2 fiber modules. Intrinsically Safe Power Channel (Ui): 9.5 Vdc, 1 A, Ci = 120 nF, Li negligible. Power Consumption: One power supply unit load. Power Dissipation: 8 W maximum. Internal & External Bus Interfaces Internal Bus (TTL): Uo = 5.4 Vdc, Io = 201 mA, Po = 1.09 W, Lo ≤ 0.45 mH, Co = 71 μF. External Bus (ControlNet): Uo = 5.4 Vdc, Io = 201 mA, AC coupled with high-pass filter (f ≥ 900 kHz). Communication Rate: 5 Mbit/s. Galvanic Isolation (per DIN EN 50020): TTL Bus / Power Supply, TTL Bus / ControlNet, ControlNet / Power Supply. Environmental & Operating Conditions Ambient Temperature: -20°C to 70°C (-4°F to 158°F). Storage Temperature: -20°C to 100°C (-4°F to 212°F). Maximum Relative Humidity: 95% non-condensing. Pollution Gas Test: Test Level G3 per ISA-S71.04-1985. Shock Test: 15g peak, 11ms duration. Vibration Test: 2g @ 10 Hz to 500 Hz per IEC 68-2-6. Protection Class: IP20 (requires IP54 or better housing for field installation). Physical Dimensions & Wiring Dimensions (H x W x D): 92 mm x 94 mm x 87 mm (3.6 in x 3.7 in x 3.4 in). Weight: 0.319 kg (0.70 lb). Wire Size (Power Terminals): 12 AWG (4 mm²) stranded max, 1.2 mm insulation max. ControlNet Cable: Belden 3092A (see Honeywell specifications for details). Standards & Certifications Conformity: DIN EN 50014:1992, DIN EN 50020:1994, DIN EN 50284:1997, DIN IEC 721, DIN EN 50081-2, DIN EN 50082-2, NAMUR NE 21. CE Conformity (Europe): TBD. CENELEC Classification: II (1) 2G EEx ia/ib IIB/IIC T4. ATEX Certification: DMT 99 ATEX E 036 X. Marked for all applicable directives. Installation Guidance Mount the Honeywell TC-PBFO01 on a DIN rail inside a suitable enclosure. Use an IP54 or higher rated housing when installing in hazardous field locations. Connect the ControlNet cables using Belden 3092A coax per Honeywell specifications. Install fiber optic modules into the two available slots as needed. Ensure all intrinsically safe connections comply with ATEX installation requirements. Package Contents One Honeywell TC-PBFO01 ControlNet repeater adapter. DIN-rail mounting clip (pre-installed). Printed quick-start guide. No certificates or warranty documents included. Shipping & Logistics We ship via FedEx, UPS, or DHL within 5 business days. All units are brand new and original stock. We keep the TC-PBFO01 in stock for immediate dispatch. Frequently Asked Questions (FAQ) Q: How many fiber modules does the TC-PBFO01 support? This Honeywell TC-PBFO01 supports up to 2 fiber optic modules. Q: What is the intrinsically safe power rating? The IS power channel provides Ui = 9.5 Vdc and Ii = 1 A with Ci = 120 nF. Q: What communication rate does this repeater support? It supports ControlNet at 5 Mbit/s with a high-pass filter at 900 kHz. Q: Is this module certified for hazardous locations? Yes, it carries ATEX certification DMT 99 ATEX E 036 X and CENELEC II (1) 2G EEx ia/ib IIB/IIC T4. Q: What operating temperature range does it support? The TC-PBFO01 operates from -20°C to 70°C (-4°F to 158°F). Q: Do you have the TC-PBFO01 in stock? Yes, we maintain stock and ship within 5 days via FedEx, UPS, or DHL. Returns are accepted within 30 days. © 2026 NexAuto Technology Limited. All rights reserved. Original Source: https://www.nex-auto.com/ Contact: sales@nex-auto.com Phone: +86 153 9242 9628