Solis 5kW 1P Low Voltage Off-Grid Inverter
The Solis 5kW 1P Low Voltage Off-Grid Inverter delivers dependable energy independence for homes, farms, and small businesses. It supports generator backup, provides 200 % overload for 10 seconds, enables fast one-click charging, and allows parallel and AC-coupling expansion. Perfect for remote or backup power applications. The Solis S6-EO1P-5-K-L 5kW 1-Phase Low Voltage Off-Grid Inverter is a high-performance solar energy solution for residential and light commercial use. Designed to work off-grid with generator backup, it ensures continuous power supply even in remote areas or during extended outages. ⚡ Key Features Generator Compatible – Seamlessly connects to a generator as a backup power source for true energy independence. High Surge Capacity – Handles 200 % overload for up to 10 seconds, protecting appliances from sudden power demands. Scalable Design – Supports parallel operation and AC coupling, letting you expand your system capacity as energy needs grow. Fast One-Click Charging – Convenient quick-charge mode speeds up battery replenishment. Flexible Battery Options – Works with multiple battery chemistries, including quick setup for non-communicating batteries. Intelligent Energy Management – Dual backup load support prioritizes critical circuits, while six TOU (Time-of-Use) settings help reduce electricity costs. Smart Monitoring – Integrated LCD and Bluetooth, with optional Wi-Fi for remote management. This inverter is the ideal choice for homes, farms, and small businesses that need reliable, off-grid power with the option to integrate solar, batteries, and generators. Technical Specifications Model: S6-EO1P-5-K-L Rated Output Power: 5 kVA / 5 kW Battery Voltage Range: 40 – 60 V Maximum Solar PV Input Power: 6.5 kW Maximum PV Input Voltage: 500 V MPPT Voltage Range: 90 – 430 V Maximum PV Input Current: 16 A / 16 A Maximum AC Charge Current: 80 A Maximum Solar Charge Current: 100 A Surge Capacity: 10 kVA (10 seconds of 200 % overload) Output Voltage / Frequency: 230 V ±1 % / 50 Hz or 60 Hz ±0.1 % Efficiency (PV to AC): Up to 96.6 % Operating Temperature Range: –10 °C to +60 °C Humidity: 5 % – 95 % non-condensing Ingress Protection: IP21 Parallel Capability: Up to 6 units Dimensions (W × H × D): 340 × 480 × 170 mm Weight: 13.8 kg Certifications: IEC 62109, IEC 61000, 55011 Warranties: All inverters and batteries must be installed by a qualified electrical wireman or Master electrician with a valid registration with the Department of Labour. A valid electrical certificate of compliance (COC) must be issued once installed, specific to the installation of the backup or solar system. The installation must be compliant with SANS 10142 and ALL its parts. Any warranty claim submitted without installation photos, a valid COC and proof of a qualified wireman/master electrician installing the unit, can be rejected and will render the warranty claim null at void