Functional Features Using these devices it is possible to interface the loop with different systems, or to activate, by means of output modules, any type of output (sounders, light signals, fire doors electromagnets, etc.). Reduced dimension permits device installation in any environment type. Devices are provided with integrated short circuit isolator, and addresses can be programmed by means of the programmer or with the addressing function of Teledata smoke detection panels. Technical Features • Monitored input able to detect different thresholds • Stand by current consumption: 130 μA • Alarm current consumption: 6mA (LED On) • Provided with integrated isolator circuit • Relay output: 30Vdc 2° • Operating temperature: –30°C + 70°C • Max. humidity.: 95% non condensing • Max. Cable cross section 2.5 mm² • Power supply: 18 ~ 27V • Dimensions:58x28x15 mm • Weight: 13g