MultiPlus-II 48/3000 35-50 120VThe MultiPlus-II is a multifunctional inverter/charger with all the features of the MultiPlus, plus an external current sensor option, which extends the PowerControl and PowerAssist functions to 100A.PowerControl & PowerAssist - Boosting the Capacity of the Grid or a Generator A maximum grid or generator current can be set. The MultiPlus-II will then take into account other AC loads and use whatever is extra for battery charging, thus preventing the generator or grid from being overloaded (PowerControl function).PowerAssist takes the principle of PowerControl to a further dimension. Where peak power is so often required only for a limited period, the MultiPlus-II will compensate for insufficient generator, shore, or grid power with power from the battery. When the load reduces, the spare power is used to recharge the battery.Solar Energy: AC Power Available Even During a Grid Failure The MultiPlus-II can be used in off-grid as well as grid-connected PV and other alternative energy systems. It is compatible with both solar charger controllers and grid-tie inverters.Two AC Outputs The main output has no break functionality. The MultiPlus-II takes over the supply to the connected loads in the event of a grid failure or when shore/generator power is disconnected. This happens so fast (less than 20 milliseconds) that computers and other electronic equipment will continue to operate without disruption.The second output is live only when AC is available on the input of the MultiPlus-II. Loads that should not discharge the battery, like a water heater, for example, can be connected to this output.Virtually Unlimited Power Thanks to Parallel, Split Phase, and Three Phase Operation Up to 6 Multis can operate in parallel to achieve higher power output. Six 48/3000/35 units, for example, will provide 15 kW / 18 kVA output power with 210 Amps charging capacity.In addition to parallel connection, two units of the same model can be connected for a 240V split-phase output, and three units of the same model can be configured for three-phase output. But that’s not all: up to 6 sets of three units can be connected in parallel per phase.On-Site System Configuring, Monitoring, and Control Settings can be changed in a matter of minutes with VEConfigure software (computer or laptop and MK3-USB interface needed).Several monitoring and control options are available: Color Control GX, Venus GX, Octo GX, CANvu GX, laptop, computer, Bluetooth (with the optional VE.Bus Smart dongle), Battery Monitor, Digital Multi Control Panel.Remote Configuring and Monitoring Install a Color Control GX or other GX product to connect to the internet. Operational data can be stored and displayed on our VRM (Victron Remote Management) website, free of charge. When connected to the internet, systems can be accessed remotely, and settings can be changed.Specifications: PowerControl & PowerAssist: Yes Transfer Switch: 50A Maximum AC Input Current: 50A Inverter Specifications: DC Input Voltage Range: 38 -66 V Output: Output Voltage 120 VAC ± 2% / Frequency 60 Hz ± 0,1% (1) Continuous Output Power at 25°C (3): 3000 VA Continuous Output Power at 25°C: 2400 W Continuous Output Power at 40°C: 2200 W Continuous Output Power at 65°C: 1700 W Peak Power: 5500 W Maximum Efficiency: 95% Zero Load Power: 11 W Zero Load Power in AES Mode: 7 W Zero Load Power in Search Mode: 2 W Charger Specifications:AC Input: Input Voltage Range 90-140 VAC / Input Frequency: 45 – 65 HzCharge Voltage 'Absorption': 57,6 VCharge Voltage 'Float': 55,2 VStorage Mode: 52,8 VMaximum Battery Charge Current: 35 ABattery Temperature Sensor: YesGeneral Specifications: Auxiliary Output: 32 A External AC Current Sensor (optional): 100 A Programmable Relay: Yes Protection: a – g VE.Bus Communication Port: For parallel, split-phase, and three-phase operation, remote monitoring, and system integration General Purpose Com. Port: Yes, 2x Remote On-Off: Yes Operating Temperature Range: -40 to +65°C (-40 – 150 °F) (fan-assisted cooling) Humidity (Non-Condensing): Max 95% Enclosure Specifications: Material & Color: Steel, blue RAL 5012 Protection Category: IP22 Battery-Connection: M8 bolts 120 V AC-Connection: Screw terminals 13 mm² (6 AWG) Weight: 19 kg / 42 lb. Dimensions (hxwxd): (mm) 572 x 277 x 147 / (inch) 22.5” x 10.9” x 5.8” Standards: Listings: UL1741 pending Safety: EN-IEC 60335-1, EN-IEC 60335-2-29, CSA 22.2 107.1-16 Emission, Immunity: EN 55014-1, EN 55014-2, EN-IEC 61000-3-2, EN-IEC 61000-3-3, EC 61000-6-1, IEC 61000-6-2, IEC 61000-6-3 *Note: For a short period of time this product was called MultiGrid-IIPlease contact your dealer for any returns, repairs or support issues related to this product. Quick Guide (pdf) Owner's Manual (pdf) Brochure (pdf)