MRCOOL GeoCool 48K BTU 4T Multi Positional 230V 1-Phase 60Hz DC Inverter Compressor (GCSHPM048IN)
MRCOOL GeoCool 48K BTU 4T Multi Positional 230V 1-Phase 60Hz DC Inverter Compressor (GCSHPM048IN) GeoCool 48K BTU 4T Multi Positional 230V 1-Phase 60Hz DC Inverter Compressor Embrace comfort with the GeoCool® all DC Inverter Technology. Equipped with the high precision Electronic Expansion Valve, allowing for more accurate temperature control while also keeping the utility bill down. The flexibility of four independent modules makes it easy to meet the installation requirements of different air outlet methods and applications. Space constraints are less of an issue when a custom built layout is an option! For a long term solution with lower maintenance costs, design your own GeoCool® Inverter Series Geothermal unit Features Up to 70 EER DC Inverter technology Closed loop - Full load - Cooling Current Input: 13 Heating Current Input: 17 || Open Loop- Full Load - Cooling Current Input: 10 Heating Current Input: 17 Open loop Operating Pressure Range: Min: 25 psi || Max: 50 psi Closed loop Operating Pressure Range: Min: 25 psi || Max: 50 psi Cooling Operating Range: Inlet: 44.6F - 107.6F || Ambient: 50F - 100.4F || Return Air: 60.8F - 89.6F Heating Operating Range: Inlet 21.2F - 89.6F || Ambient: 39.2F - 84.2F || Return Air: 50F - 80.6F Open loop - Full load - EER: 27.02 COP: 4.2 || Open Loop- Part Load - EER: 70.97 COP: 6.2 Closed loop - Full load - EER: 18.29 COP: 3.4 || Closed Loop- Part Load - EER: 48.79 COP: 5.1 Full Fluid Flow (GPM): 7.93 || Partial Fluid Flow (GPM): 7.93 Open loop - Full load - Cooling Capacity: 50500 BTU Heating Capacity: 48000 BTU || Open Loop- Part Load - Cooling Capacity: 13300 BTU Heating Capacity: 11000 BTU Closed loop - Full load - Cooling Capacity: 46500 BTU Heating Capacity: 40000 BTU || Closed Loop- Part Load -Cooling Capacity: 14500 BTU Heating Capacity: 9800 BTU Dimensions 22.44" D x 25.12" H x 24.80" W Net Weight 231.53 lbs EER Up to 70 Cooling Capacity (BTU) Up to 50500 Heating Capacity (BTU) Up to 46500 Voltage (V) 208 / 230 Phase 1 Cycle 60 Max Fuse Breaker (A) 35 Min Circuit Ampacity (A) 26 Refrigerant Type R-410A Inverter DC Overload Protection Yes Energy Star Certified Yes AHRI Certified Yes Base Parts Warranty 10 Years Base Labor Warranty 5 Years Limited Has Batteries No Contains Chemicals Yes Contains Aerosol Yes Contains Compressed Gas Yes Proposition 65 Warning Yes Brochure Install Manual Service Manual Warranty Doc