Eemax SPEX95T LavAdvantage Tankless Water Heater 9.5kW 240V
Eemax SPEX95T LavAdvantage Tankless Water Heater 9.5kW 240V Brand: Eemax | SKU: SPEX95T Product Overview The Eemax SPEX95T LavAdvantage is a 9.5kW, 240V point-of-use electric tankless water heater for compatible lavatory and low-flow fixture applications. It is intended to deliver on-demand hot water near the point of use when the fixture flow and required temperature rise fit the heater's operating range. The stored specifications list 0.2 GPM minimum activation, 3.0 GPM maximum flow, 3/8 in. integral compression fittings, and a 30 PSI to 150 PSI pressure range. The unit may be used on 208V with reduced temperature output, so the site voltage should be confirmed before selection. Before ordering, verify the fixture aerator or flow control, incoming water temperature, target outlet temperature, breaker size, wire size, plumbing connections, mounting location, and indoor freeze protection. Do not select the heater by maximum flow alone, and do not energize the unit until water has been flushed through it and all air has been purged. Key Features: 9.5kW point-of-use tankless water heater 240V operation Can be used on 208V with reduced output 0.2 GPM minimum activation flow 3/8 in. integral compression fittings Compact indoor format Common Uses: Compatible handwashing lavatories Office restrooms and low-flow point-of-use sinks Commercial or residential fixtures where the heater is properly sized Technical Specifications: Model: SPEX95T Power Rating: 9.5kW Voltage: 240V; can be used on 208V with reduced temperature output Minimum Activation Flow: 0.2 GPM Maximum Flow: 3.0 GPM Water Connections: 3/8 in. integral compression fittings Pressure Range: 30 PSI minimum / 150 PSI maximum Dimensions: 9.75 in. H x 5.25 in. W x 3 in. D Location: Indoor use; protect from freezing Compatibility and Installation Notes: Confirm voltage, fixture flow, temperature rise, circuit capacity, plumbing connection size, and indoor installation requirements before purchase. Do not use in a recirculation loop unless the manufacturer manual specifically allows it. FAQ What flow activates this heater? The listed minimum activation flow is 0.2 GPM. Can it be used on 208V? Yes, but output is reduced compared with 240V operation. What connections does it use? It uses 3/8 in. integral compression fittings. Why Buy From Big Frog Supply? Big Frog Supply provides clear product information, helpful support, and convenient online ordering for water-heating equipment.