LuxpowerTek GEN Series 16kW Hybrid Inverter 25kW PV Input
SKU: LXP-GEN-LB-US-16K Mfg. SKU: GEN-LB-US-16K LUXPower LXP-GEN-LB-US-16K Hybrid Split-Phase Solar Inverter Off-Grid & Grid-Tie | Pure Sine Wave | 3 Integrated MPPT Controllers Power your Canadian home, remote cabin, or commercial space with the LUXPower 16K hybrid inverter. This transformer-less unit delivers up to 12 000 W continuous output (16 000W with PV support), supports split-phase 120/240 V and three-phase 120/208 V, and integrates a high-efficiency MPPT charge controllers—perfect for coast-to-coast solar, backup, and off-grid systems in Canada. Key Features & Benefits 12 kW Continuous & 25 kW PV Input Runs whole-house loads and off-grid cabins; harvests solar from up to 25 000 W of panels across three MPPT channels. Split-Phase & Three-Phase Output Native 120/240 V split-phase or 120/208 V three-phase support for North American wiring—no external transformer required. (Three-phase requires 3 units) Ultra-Fast UPS Switching (< 20 ms) Keeps critical loads (refrigerator, furnace, medical devices) online during grid outages. Advanced MPPT Charge Controller Three independent MPPT inputs (2 × 11 440 W, 1 x 6 600W) with up to 99.9 % tracking efficiency—maximizes solar harvest under Canada’s varied light conditions. 2 x 26A input/31A Isc, 1 x 15A input/19A Isc Robust Safety & Compliance Built-in protections (reverse polarity, over-current/voltage, anti-islanding, AFCI, RSD, surge) and certified to UL1741SA, UL1741SB,CSA22.2, UL1741PCS CRD, CEC, FCC Part15B, IEEE1547.1. User-Friendly Color Touchscreen 7″ LCD display plus RS485, Wi-Fi, and CAN interfaces for real-time monitoring and remote management from coast to coast. Durable Design for Canadian Climates Transformer-less, fan-cooled (< 50 dB), operates from –25 °C to +60 °C; handles humidity up to 100 % and altitudes to 2 000 m. Technical Specifications Specification Details Model LXP-GEN-LB-US-16K Continuous Output Power 12 000 W Max PV Input Power 25 000 W MPPT Inputs 3 (2 @ 11 440 W, 1 @ 6 600W) DC Input Voltage Range 120–550 V Startup Voltage 140 V Nominal DC Input Voltage 360 V Full-Power MPPT Range 120–440 V Max DC Input Current/MPPT 26 A / 31 A, 15 A / 19 A AC Output Voltage 120/240 V split-phase; 120/208 V three-phase Nominal AC Output Current 66.7 A UPS Transfer Time < 20 ms Battery Voltage Range 40–60 V (nominal 48 V) Max Charge/Discharge Power 12 000 W Max Charge/Discharge Current 250 A Efficiency ≥ 97.5 % (CEC), MPPT ≥ 99.9 % Cooling Method Variable-speed fan (< 2 000 m elevation) Operating Temperature –25 °C to +60 °C Storage Temperature –25 °C to +60 °C Humidity 0–100 % RH Ingress Protection IP 66 / NEMA 4X (outdoor rated) Dimensions (W × H × D) 566 × 893 × 285 mm / 22.3 × 35.2 × 11.2 in Weight 57 kg / 125.7 lbs Display & Interface 7″ Color touchscreen, RS485, Wi-Fi, CAN Certifications UL 1741SA, UL 1741SB, CSA C22.2, CEC, FCC Part15B, IEEE 1547.1, HECO SRD V2.0, System: UL9540 with PSHIELD MAX Battery, UL1741PCS CRD, FCC SDOC, NEC 690.12 Warranty 10 years Why Buy from Solar Super Store? Fast Shipping Across Canada — coast-to-coast delivery Canadian-Based Expert Support — tailored advice for your province’s grid and conditions Full Manufacturer Warranty — 10 years of coverage from LUXPower Systems Ensure reliable, high-performance solar and backup power for your Canadian home or cabin.