Victron SmartSolar MPPT RS 450/200 200A solar charge controller with 4 independent MPPT inputs for 48V systems (Bluetooth inbuilt) (SCC145120512)
Victron Energy SmartSolar MPPT RS Series Victron SmartSolar MPPT RS 450/200 Solar Charge Controller 200A Output | 4 Independent MPPT Inputs | For 48V Systems The Victron SmartSolar MPPT RS 450/200 is an advanced solar charge controller engineered for high-voltage PV arrays and large 48V battery systems. This robust unit features four independent Maximum Power Point Tracking (MPPT) inputs, allowing for optimal energy harvest even from complex or partially shaded solar installations. Designed for both off-grid and grid-connected battery systems, the 450/200 model delivers a substantial 200A charging output, making it suitable for demanding residential, commercial, and industrial applications. Its integrated Bluetooth and VE.Can/VE.Direct communication ports provide comprehensive monitoring, configuration, and seamless integration with other Victron Energy devices. SYSTEM COMPATIBILITY: Optimised for 48V battery banks, supporting a wide range of battery chemistries including Lithium, AGM, Gel, and Tubular Plate. Key Features ▶ Ultrafast MPPT Technology — Maximises energy harvest from solar arrays by quickly tracking the Maximum Power Point. ▶ Four Independent MPPT Inputs — Optimises performance for complex arrays with varying orientations, tilt angles, or shading. ▶ 200A Charge Current for 48V Systems — Delivers substantial power for rapid and efficient charging of large battery banks. ▶ Wide PV Input Voltage Range (65-450V) — Accommodates high-voltage solar panel strings, reducing cabling losses. ▶ Integrated Bluetooth & VE.Can/VE.Direct — Enables advanced monitoring, configuration via VictronConnect App, and seamless system integration. ▶ Built-in LCD Display — Provides clear, real-time monitoring of key system operating parameters and diagnostics. ▶ Programmable Relay — Allows for custom automation, such as generator start or low battery alarm signals. ▶ Comprehensive Electronic Protection — Ensures safe and reliable operation against various electrical faults. Technical Specifications Parameter Value Battery Voltage 48V (Programmable 36V-60V) Rated Charge Current 200A Max. DC PV Voltage 450V Start-up Voltage 120V MPPT Operating Voltage Range 65V - 450V Number of Trackers 4 Max. PV Operational Input Current (per tracker) 16A Max. PV Short Circuit Current (per tracker) 20A Max. PV Array Size (per tracker) 7200 Wp (450V x 20A) Max. DC Output Charging Power (total) 11520W Efficiency > 95% Communication Ports VE.Direct, VE.Can, Bluetooth Programmable Relay AC Rating 240VAC / 4A Programmable Relay DC Rating 4A up to 35VDC, 1A up to 70VDC Operating Temperature Range -40°C to +60°C Enclosure Protection IP21 Dimensions (H x W x D) 487 x 434 x 146 mm Weight 13.7 kg Charging & Battery Modes Feature Description Battery Compatibility Compatible with a wide range of 48V battery types, including AGM, Gel, Tubular Plate, and Lithium (LiFePO4). Programmable Charge Algorithm Fully programmable charge settings for absorption voltage, float voltage, equalisation, and tail current to match battery manufacturer specifications. Temperature Compensation Includes a battery temperature sensor for automatic charge voltage compensation, optimising battery health and lifespan. Synchronised Parallel Operation Up to 25 units can be daisy-chained via VE.Can, allowing for synchronised charge stages across multiple controllers for very large systems. Typical Applications Application Description Large Off-Grid Systems Ideal for remote homes, cabins, or industrial sites requiring substantial 48V battery charging from high-voltage solar arrays. Grid-Connected Battery Systems Suitable for energy storage systems that integrate with the grid, providing backup power or optimising self-consumption. Commercial & Industrial Installations Provides reliable and efficient solar charging for businesses, agricultural setups, or telecommunication sites. Advanced Mobile & Marine Systems Powers large RVs, yachts, or specialist vehicles with extensive 48V electrical demands and high-power solar arrays. Built-In Protection Functions The Victron SmartSolar MPPT RS 450/200 incorporates comprehensive electronic protection features for safe and reliable operation. These include protection against PV short circuit • PV reverse polarity • PV overvoltage • PV overcurrent • reverse current from battery to PV • battery overvoltage • battery reverse polarity • and overheating. The unit also features self-diagnostic capabilities with LED fault indicators for quick troubleshooting. Common Questions What battery types are compatible with this controller? The Victron SmartSolar MPPT RS 450/200 is compatible with all common 48V battery chemistries, including Lithium (LiFePO4), AGM, Gel, and Tubular Plate batteries. Its charging algorithm is fully programmable to match specific battery manufacturer requirements. How does the 4-MPPT design benefit my solar array? The four independent MPPT inputs allow you to connect separate strings of solar panels, each operating at its optimal power point. This maximises energy harvest, especially when panels are installed at different orientations, tilt angles, or experience varying levels of shading. Can I monitor this controller remotely? Yes, the controller has built-in Bluetooth for wireless connection to the VictronConnect App on your smartphone or tablet. It also features VE.Direct and VE.Can ports for wired communication with Victron GX devices and the Victron Remote Management (VRM) portal for advanced remote monitoring and control. What is the maximum solar array size I can connect? Each of the four MPPT trackers can handle up to 7200 Wp (Watt-peak) of solar input, with a maximum operational PV input current of 16A per tracker. The total maximum DC output charging power for the unit is 11520W. Installation Notes Installation should be carried out by a qualified professional to ensure safety and compliance with local electrical regulations. Ensure adequate ventilation around the unit, as it features active cooling. Always follow the wiring instructions provided in the official Victron Energy manual for correct and safe connection of PV arrays and batteries. Verify PV array voltage and current are within the controller's specified limits before connection. Proper grounding of the system is essential for safety and optimal performance. Before You Buy Confirm your battery bank voltage is 48V to ensure compatibility with this controller. Calculate your total PV array power and voltage to ensure it falls within the controller's input specifications (Max 450V VOC, 11520W total output). Consider your system's communication needs; this unit integrates well with other Victron GX devices via VE.Can. Review the official Victron Energy product manual for detailed technical information and installation guidelines. For complex installations, consult with a certified solar installer or system designer. All specifications are based on manufacturer data and are subject to change. Always refer to the official product documentation for the most accurate and up-to-date information. This product is covered by a 5-year warranty.