Dyness PowerBrick MAX 16.07kWh Lithium Battery - 51.2V
🔋 Dyness PowerBrick Max 16.07kWh Lithium Battery – 51.2V 🆔 Model Battery: Dyness PowerBrick Max Lithium Battery – 16.07kWh 📦 Includes Dyness PowerBrick Max Battery Unit Integrated Battery Management System (BMS) Mounting support (Wall or Floor Installation) Contents Inside the Box Battery Brackets (Left & Right) 2 × Fixing Brackets 50mm² Battery Cables (Red & Black) – 2.005m 6 × Expansion Bolts 3 × Mounting Screws Positioning Cardboard 6mm Ground Wire (50cm) Communication Cables CAN Resistor Unlock Piece (Black) Warranty Card Customer Letter Top Cover ⚡ Key Features Large 16.07kWh energy storage capacity with high usable energy output. High-capacity 314Ah LiFePO₄ battery cells for exceptional lifespan. Supports up to 50 batteries in parallel, providing scalable storage up to approximately 803kWh. High charge and discharge capability of up to 200A. Integrated intelligent Battery Management System (BMS) with comprehensive protection functions. Optional self-heating function available for cold-climate installations. IP20-rated enclosure designed for indoor installations. Flexible wall-mounted or floor-mounted installation. Built-in Wi-Fi monitoring with mobile App support for real-time system management. Compatible with a wide range of leading inverter brands. Long service life with 8,000+ operating cycles. 📐 Specifications Specification Details Battery Type LiFePO₄ (Lithium Iron Phosphate) Nominal Energy 16.07 kWh Usable Energy 15.27 kWh Nominal Capacity 314 Ah Nominal Voltage 51.2 V Operating Voltage 44.8 – 57.6 V Depth of Discharge 95% ⚙️ Performance Specification Details Recommended Charge/Discharge Current 140 A (0.45C) Maximum Charge Current 200 A Maximum Discharge Current 200 A Peak Discharge Current 300 A (2 minutes) Recommended Output Power 7.168 kW Maximum Charge Power 10.24 kW Maximum Discharge Power 10.24 kW Cycle Life ≥8,000 Cycles 🛠️ Technical & Build Specification Details Battery Management Integrated Smart BMS Communication CAN / RS485 Monitoring Wi-Fi & Mobile App IP Rating IP20 Operating Temperature (Charge) 0°C to 55°C (Optional heating available for colder environments) Operating Temperature (Discharge) -20°C to 55°C 📏 Physical Specifications Specification Details Dimensions (W × D × H) 435 × 235 × 850 mm Weight 119 kg Installation Floor-mounted or Wall-mounted 🔄 Compatibility Compatible with leading inverter brands including: Deye Victron Energy SMA Growatt GoodWe Solis LuxPower Sunsynk And many other CAN/RS485 compatible inverters. Ideal for: Residential solar systems Commercial energy storage Hybrid inverter installations Backup power systems Off-grid energy storage ℹ️ Additional Information Expandable to 50 battery units in parallel. Optional accessories include a self-heating module and top cover. Designed for indoor energy storage applications. Professional installation is recommended for optimal performance and safety. 🏷️ Quality & Support The Dyness PowerBrick Max 16.07kWh delivers dependable, high-capacity energy storage for residential and commercial solar systems. Featuring premium LiFePO₄ technology, intelligent battery management, and exceptional scalability, it provides reliable long-term performance while supporting a wide range of hybrid and backup power applications. With over 8,000 operating cycles and compatibility with many leading inverter brands, the PowerBrick Max is an ideal solution for expanding energy independence in indoor installations. SPEC SHEET