2550 Litre Steel Bunded Generator Bulk Tank
2550 Litre Steel Bunded Generator Bulk Tank | TAN.GBI-2806 Effective, compliant fuel storage for backup generator systems The GBI-2806 is a robust 2,550 litre steel bunded fuel tank. It’s ideal for use as a reliable bulk storage solution for diesel-powered generator systems. Engineered to meet BS799 pt5 standards, this commercial-grade Generator Bulk Imperium ® tank is a perfect fit for installations where uptime is critical. It excellently suits commercial premises, remote infrastructure, and emergency backup sites requiring secure, mid-capacity fuel storage. Made to Order Diesel Storage at a Reasonable Price Our 2,550 litre generator bulk tank is highly customisable to your specifications. Its construction follows a proven, interactive process which starts with your enquiry and our full understanding of your application and technical requirements. We swiftly follow with prompt quotes and custom drawings where necessary. We will also guide you through the relative merits of this tank’s optional extras. This means that you’ll be completely comfortable with your choice of generator fuel tank and accessories selection. We hope you’ll like our competitive prices too. Key Features at a Glance Nominal capacity: 2,076 litres Useable capacity (with OPV): 2,010 litres 10-year warranty (subject to maintenance as per manual) Bunded design – 110% containment to meet strict environmental compliance Full-size front-mounted security cabinet – 650mm deep, ventilated, featuring a lockable swing door (with options for a roller shutter upgrade) Lockable top box – Small, secure enclosure housing the tank probe sockets High-performance anti-corrosive finish – Zinfoss 340 WS system with ST2 surface preparation, finished in your choice of RAL colour Comprehensive port setup – Top and bottom feed/return ports for generator, pump, and fuel polishing setups 610mm manway inspection hatch – Complete with gasket, bolted lid, and integrated handles Lifting eyes – 4 structurally integrated points for ease of transport (empty only) Earthing bolt – To easily connect a ground wire for electrical safety Tank & Bund Construction The GBI-2806 features a double-skinned design, comprising an inner primary tank enclosed within an outer bunded tank. This configuration provides 110% containment of the total liquid being stored, ensuring compliance with environmental regulations and safeguarding against potential leaks. The tank is constructed from heavy-duty structural plate steel to BS EN 10025-2:2004 S275JR, incorporates internal tank bracing (BST design), and is mounted on full-width bearers for maximum structural stability. The outer tank serves as a protective barrier, offering secondary containment in the unlikely event of inner tank failure. Fuel Compatibility This tank is suitable for the safe storage of a wide range of fuels including: White diesel (DERV) Red diesel (gas oil) Heating oil Hydrotreated Vegetable Oil (HVO) Always check with your fuel supplier for compatibility if using additive blends or alternative fuels. Compliance All Atlantis Generator Bulk Tanks are built in accordance with BS799 Part 5 with required internal tank bracing. Each tank incorporates a bunded outer shell with a minimum 110% capacity, ensuring full compliance with environmental safety standards. This 2,550 litre tank is manufactured to comply fully with: The Water Environment (Oil Storage) (Scotland) Regulations 2006 The Control of Pollution (Oil Storage) (England) Regulations 2001 SEPA & EA Guidelines This tank also includes a secure fill point with a non-return valve and drip tray as standard inside the cabinet—helping prevent spills, overfills, and costly downtime during installation or servicing. Technical Highlights | 2,550 Litre Generator Bulk Tank Outer tank dimensions: 2580mm (L incl. full cabinet) x 1320mm (W) x 1250mm (H) Inner tank dimensions: 1800mm (L) x 1260mm (W) x 1248mm (H) Brimful capacity: 2186 litres Nominal capacity: 2076 litres Useable capacity (c/w OPV): 2010 litres Dry weight (approx): 399 kg Wet weight (full, approx): 2700 kg Material: Structural steel grade S275JR meeting the BS EN 10025-2:2004 standard Finish: Surface preparation ST2 followed by a Zinfoss 340 WS solvent-borne, high-performance, anti-corrosive one-coat system. Multi-surface, self-priming mid-sheen topcoat (50% gloss), applied at 150μm WFT / 75μm DFT. Marine Environments: While our Zinfoss paint is extremely robust, an alternative specialized paint system is recommended if the tank is to be located in a marine environment. Please speak to our sales team for more info. Colour: TBC (Select your preferred tank colour from the RAL colour chart) Mounting: Full-width base bearers Supplied as Standard – Fittings & Connections 1 x 2″ fill point (inside cabinet), c/w lever ball valve, non-return valve & drip tray 1 x 2″ tank-to-bund vent 1 x 2″ bund-to-atmosphere vent 1 x 1″ pump feed (inside cabinet) – requires removable drop tube, quoted separately below 1 x 1″ pump return (inside cabinet) 1 x 1″ spare return (inside cabinet) 1 x 1″ top feed for fuel polisher (inside cabinet) – requires removable drop tube, quoted separately below 1 x 1″ top return for fuel polisher (inside cabinet) – terminating at rear of cabinet 1 x 1″ top suction port for sludge drain (plugged) 1 x 1″ bottom outlet c/w internal isolation valve & T-bar handle 1 x Flange fitted to cabinet for double-skin pipework entry (flange type TBC) 2 x 1.5″ tank sockets (inside cabinet) 1 x 1.5″ bund socket (rear of tank) Tank Assembly Pack: Includes cap & chain, labelling kit, and isolation fittings Optional Extras Roller Shutter Cabinet Door – Lockable, replaces the standard swing door Removable Drop Tubes – Fitted inside the tank for suctioning contents during maintenance (required for the pump feed and fuel polisher feed ports) 2″ Overfill Prevention Valve – Automatically halts filling to prevent overflows Hydrostatic Contents Gauge – Pneumatic fuel contents gauge with percentage readout O.L.E C2020 Gauge Kit (230v) – With high/low alarm and backlit tank level display O.L.E T5020 Gauge Kit (230v) – BMS-compatible, highly accurate, continuous readout gauge High/Low Level Probe – Bund or tank level sensor for integration with O.L.E. Alarm Kits Piusi Ocio Fuel Tank Level Gauge – Versatile display options MultiComp Fuel Tank Alarm (230V) – c/w 3 probes & 3 relays 50 LPM or 100 LPM Duplex Fuel Pump Set & Control Panel – BMS compatible control panel for auto fuel transfer to a client day service tank or slab tank 50 LPM Simplex Fuel Pump (230V) & Control Panel – Incorporates a digital flow meter and BMS compatible control panel SRFA-S2-R 25mm Electrically Actuated Ball Valve 50 LPM or 100 LPM Fuel Polisher & Control Panel (230V) – Designed to maintain fuel at the clean oil standard ISO 4406:2017 18/16/13 particle count / less than 200 ppm water content Electrical Installation Pack – Connecting the electrical supply to fuel transfer equipment Mechanical Installation of Fuel Transfer Equipment (1 or 2 appliances) – Includes fitting, pressure testing, and factory commissioning Manual & Powered Emergency Dispensing options – Manual Semi-Rotary Diesel Hand Pump Kit or 230v 50 LPM Diesel Piusi Pump Kit Applications Backup power systems: Commercial buildings, mid-sized data centres, and healthcare facilities Remote installations: Safe fuel supply for off-grid or hard-to-reach infrastructure sites Emergency services: Supporting critical local infrastructure and emergency response hubs Industrial operations: Dependable fuel delivery for plant, processing equipment, and primary machinery Contact Us Please contact our made-to-order tank specialist if you require any further information: 0330 999 1100. Or use our contact form if you prefer. We look forward to helping you with your next power generation project.