S&P Silent 100 CRZ Wall Fan - Timer / Indicator / Shutte - Rated 26l/s
Product Part Number SILENT-100-CRZ Product Overview The S&P SILENT-100 CRZ is a quiet-running 100mm axial extract fan designed to remove humid, stale air and odours from bathrooms, toilets, en-suites and other small domestic spaces. It is suitable for wall or ceiling mounting and connects to standard 100mm circular ducting. Window installation is also possible when used with the appropriate optional window kit. The fan includes an adjustable run-on timer that allows it to continue operating for between approximately 1 and 30 minutes after the connected switch has been turned off. This helps clear remaining moisture and odours after the room is no longer in use. Its motor is mounted on specially designed silent elastic blocks, which absorb vibration and help prevent noise from being transferred into the surrounding wall or ceiling. This allows the fan to deliver an airflow rate of 95m³/h while maintaining a low sound pressure level of 26.5dB(A). The SILENT-100 CRZ also includes a pilot operation light and an automatic back-draught shutter, which helps prevent outside air from entering the room when the fan is switched off. Long-life ball bearings, thermal overload protection and an IP45-rated housing provide reliable performance across different mounting positions. Technical Specification Manufacturer: Soler & Palau Product Range: SILENT Fan Type: Low-noise axial extract fan Application: Bathrooms, toilets, en-suites and other small domestic spaces Installation: Suitable for wall or ceiling mounting Window Installation: Possible with the optional SILENT-100 window kit Duct Connection: 100mm diameter Maximum Airflow: 95m³/h Maximum Airflow: Approximately 26.4l/s Listed Rated Airflow: 26l/s Fan Speed: 2,400rpm Maximum Power Consumption: 8W Supply Voltage: 230V Frequency: 50Hz Sound Pressure Level: 26.5dB(A) at 3 metres under free-air conditions Run-On Timer: Yes Timer Adjustment Range: Approximately 1–30 minutes Operation Indicator: Pilot light Back-Draught Shutter: Automatic back-draught shutter Humidity Sensor: No PIR Movement Sensor: No Motor Bearings: Long-life ball bearings Motor Mounting: Vibration-absorbing silent elastic blocks Motor Protection: Thermal overload protection Electrical Insulation: Class II IP Rating: IP45 Maximum Air Temperature: 40°C Housing Material: Injection-moulded plastic Colour: White Front Dimensions: 158mm × 158mm Overall Depth: 109.3mm Rear Casing Depth: Approximately 84.6mm Installation Depth: 79mm Spigot Diameter: 98.9mm Weight: Approximately 0.57kg