134CFM Refrigerated Air Dryer for 15HP & 20HP & 30HP Air Compressors, 1PHASE 115V, Refrigerated Air Compressor Dryer, Compressed Air Systems, Industrial Refrigerated Compressed Air Dryer
Features： 1. Air handling capacity: 134 CFM, pressure dew point: 37.4-50°F. 2. Standard working pressure: 101.5 PSI, maximum working pressure: 145 PSI. 3. Air inlet temperature: ≤140°F, ambient temperature: ≤100.4°F. 4. Adaptation to the work system: continuous work, import and export pipe size: NPT 1". 5. 134CFM Refrigerated Air Dryer for 15HP & 20HP & 30HP Compressors. 134 CFM Refrigerated Air Dryer for 15 HP, 20 HP and 30 HP Compressors, NPT 1", 115V 1-Phase 60HZ Designed for industrial and workshop compressed air systems, this 134 CFM refrigerated air dryer is built to handle high airflow and continuous operation under demanding working conditions. With an air handling capacity of 134 CFM and a pressure dew point range of 37.4–50°F, the dryer effectively removes moisture from compressed air lines, helping protect pneumatic tools, production equipment, and downstream systems from corrosion and condensation. It supports a standard working pressure of 101.5 PSI and a maximum working pressure of 145 PSI, covering most industrial compressed air applications. This unit is specifically matched for air compressors in the 15 HP, 20 HP, and 30 HP range, including rotary screw compressors and high-duty piston compressors operating at standard pressures. Standard NPT 1" inlet and outlet connections ensure unrestricted airflow and easy system integration. Powered by 115V / 1-Phase / 60Hz, the dryer is suitable for workshops and industrial facilities that require higher airflow capacity. Key Components & Functional Design Engineered for Stable Moisture Removal in Continuous Operation This refrigerated air dryer features a compact and service-friendly structure designed for continuous-duty operation. The user-friendly control panel allows operators to monitor system status and operating conditions easily. Standard NPT 1" air inlet and outlet ports provide compatibility with larger compressed air pipelines commonly used in higher-capacity systems. An electronic blowdown valve automatically discharges condensed moisture, eliminating manual drainage and helping maintain stable drying efficiency. Designed for industrial environments, it delivers reliable moisture control for mid- to high-capacity compressed air systems. Key Features, Construction & Application Overview 134CFM Refrigerated Air Dryer 1Phase 115V For Air Compressor Air handling capacity 134 CFM Pressure Dew Point 37.4-50°F Standard Working Pressure 101.5 PSI Maximum Working Pressure 145 PSI Air inlet temperature ≤140°F Ambient Temperature ≤100.4°F Adaptation to the work system Continuous work Pressure Loss ≤2.9PIS Blowdown valve Electronic blowdown valve Cooling method Air cooling Refrigerant R410a power supply V/PH/Hz 115V AC, 1 PHASE, 60HZ Cooling power 1 HP Fan power 75 W Import and export pipe size NPT 1" Product Dimension 28.74 x 15.74 x 29.13 in Net Weight 136.69 lbs Pacakge Dimension 31.49 x 18.50 x 36.22 in Gross Weight 177.47 lbs
Only ship from USA warehouse to USA(PR/AK/HI/GU/AA/AE/AP and PO BOX are not avaliable)