24,000 BTU Air Handler Hyper Heat(Outdoor)
Contractor pricing available - Please email to inquire about contractor pricing. 208-230V 24,000 BTU Multi-Position Air Handler Recommended for spaces 700 - 1200 Sq Feet Description Model 24K BTU 208-230V - Indoor GHA24H52ACXL05 24K BTU 208-230V - Outdoor GHO24H52ACXL05 Download The Product Specification Sheet Certificate Of Product Ratings Model 24,000 BTU Type Cooling & Heating Control Type Wired Controller Power Supply 208-230V~/60Hz/1P Rated Cooling Capacity BTU/h 24000 Rated Heating Capacity BTU/h 24000 SEER2 Btu/W.h 19 HSPF Rating (Region IV) Btu/W.h 9.5 EER Btu/W.h 11 COP W/W 3.4 Maximum Fuse Size A [ODU/AHU] 30/6 Outdoor Noise Level dB(A) 57 Connecting Pipe Gas Inches 3/8" Liquid Inches 5/8" Connection Wiring Power Wiring （Outdoor） mm2 3x2.5 AWG 12 Power Wiring （Indoor） mm2 3×1.0 AWG 18AWG Signal Wiring mm2 2×0.5 AWG 22AWG Suitable Area m2 65-111 Net Dimension (HxWxD) Indoor Inch 45x17.5x21 Outdoor Inch 31-13/16 x 41-3/16 x 17-15/16 Net Weight Indoor kg/lbs 51/112 Outdoor kg/lbs 67/148 Refrigerant R32 Factory Charged Volume OZ / g 81.13 / 2300 Maximum Line Length (m/ft) 50/164 Maximum Height Difference Between Indoor and Outdoor (m/ft) 30/98 Ambient temperature °F -13° to 126° **Bulk orders and volume discounts available upon request**